This operation mode is intended for connecting one or two networked lock cylinders, which control relay output K1.
An example use case is an alarmed door, or a door where a magnet lock is bypassed by a valid key insertion to the lock cylinder.
Opening the cylinder with a valid key, or activating the push button, activates relay output K1 that bypasses the door magnet contact, or opens the magnet lock, for a fixed time of 3 seconds.
In this case:
The table below describes the inputs controlling outputs K1 and K2 and whether the outputs are calendar-controllable, and if door status can be connected to the input.
Table 1. Operation Mode 8
You can connect any potential-free contact information, such as a magnetic door contact, to IN2. In this way, you can request for the door status information through iLOQ Manager and view the event log on the door status. If you have to obtain status information from, for example, both the lock strike plate and the door, you can serial connect the lock and door contacts. In this case, the status indicates whether the door is closed and locked, or not.
You can deploy this installation according to the instructions in Connecting a Remotely Managed Lock Cylinder. However, set the OPTIONS dip switches as follows: