This operation mode is intended for connecting a Key Reader or RFID reader, for controlling an alarm system.
An example use case is a door where an alarm system is controlled by a reader. A valid key activates the impulse for relay output K1 that is connected to the alarm system. If you connect the Key Reader N103, you can connect the alarm system status information to control the lowermost light of the Key Reader, to indicate the alarm system status. Connect the alarm system status information to the Door Module IN 1 to control green light, and/or IN 2 to control red light. The status information you bring from the alarm system must be potential-free. If you have connected IN2, you can request for the alarm status information through iLOQ Manager and view the event log on the alarm status.
In this case, the Door Module is programmed.
The table below describes the inputs controlling outputs K1 and K2 and whether the outputs are calendar-controllable, and if alarm status can be transferred to iLOQ Manager.
Table 1. Operation Mode 5
|K1||K2||N103 STAT2 GREEN||N103 STAT2 RED||ALARM STATUS|
You can deploy this installation according to the instructions in Controlling an Alarm System by a Key Reader or RFID Reader. However, set the OPTIONS dip switches as follows: